I purchased an Enphase M250 microinverter (pictured in the image above mounted to the back of the solar panel) and then bolted some angle brackets to the panel to create a wall mounting system. I gave a great deal of thought on how to install this panel safely and called in my friends and neighbor to help install it. Thanks to my careful planning the installation took less than an hour and went like clockwork.
We got 2 very long ladders up and then mounted 4 brackets I had made to the wall. I made a wooden jig that to ensure they were spaced correctly. Then we hauled the panel up by dropping a rope from the attic window and secured the top of the panel with two bolts. We were able to push the bottom edge of the panel out from the second floor bedroom window with a long board that I notched at the end for the purpose. This made it easier for the two guys on the ladder to bolt on the struts that hold the panel out at an angle of around 39° from the wall. I chose this angle to optimize winter performance (we are at 44° latitude here in Maine).
Before the installation, I had pulled some 14/3 Romex from a junction box in the attic down to the breaker box in the basement. I added a 15 amp 240 V dual breaker for the solar panel. The following morning at around 10:30 I clipped my Amp meter onto one of the wires and got a reading of .688 A on one of the lines - so that's 144 W.
Watts for the last 3 days:
My costs were relatively minimal:
$100 Schuco MPE 245 solar panel
$144 Enphase M250 micro inverter
$29 Enphase Engage cable
$20 Enphase M215 branch Terminator
$20 30ft 14/3 Romex wire (run to the breaker box)
The other advantage of installing this panel above my bedroom windows is that it will provide shade during the summer. I do use a small window air conditioner occasionally in July and August and this should reduce the need to use that a little.
Many thanks to my neighbors and friends who are all energy mavens:
John Rogers, experienced home builder and fine furniture maker.
Topher Belknap, home energy auditor and building efficiency expert.
Al Heath, experienced home builder and energy auditor.
We all had a lot of fun installing this panel and I could not have done this without their help.
Update a week laterI decided not to invest in an Enphase EMU Communications Gateway monitoring device for this single panel because it would cost more than the panel and microinverter at around $500. I have one of these in my workshop to provide live to the web monitoring of all 31 solar panels. It receives data over the AC power line from each microinverter and sends it out to the web portal, but it is too far from by new panel (about 150ft of wire run) so the AC signals cannot reach it..
|Enphase ENV-120M Envoy Energy Management Unit|
It shows instantaneous Watts on the lower left corner and cumulative Watt hours on the lower right corner. I plan to log the kilowatt hours weekly so that I can track performance of this single panel. If anything should go wrong, I would certainly notice a lack of performance by the end of the week. Here's a photo of it mounted above my circuit breaker box